Primary clarifier performance is measured by a tank’s total suspended solids (TSS), biological oxygen demand (BOD) and by the condition of the primary sludge, considering its volume, concentration, and septicity. When functioning as it should, a primary clarifier is expected to remove 90% to 95% of settleable solids (sludge), 40% to 60% of suspended solids (scum), 25% to 75% of bacteria and 25% to 50% of total BOD.
Organic measurement, such as BOD and chemical oxygen demand (COD) were developed to measure water quality. However, these methods are time consuming, ranging from hours to days, which limits how useful COD or BOD can be as process control parameters. That’s where total organic carbon (TOC) comes in. TOC allows for effective process control because results are generated much more frequently, which means that decisions concerning clarifier performance and efficiency can be made almost in real-time and more smartly.
Various factors affect clarifier efficiency, such as the type of solids in wastewater and where they come from, how long it takes to travel through the system, hydraulic detention time, the design of the tank and the condition of the equipment as well as the temperature of wastewater.
Temperature affects all biological processes. Optimum temperatures for bacterial activity are in the range of 25 °C to 35 °C. Biological oxidation rates peak at about 35 °C in most treatment systems. At temperatures higher than 35 °C, treatment efficiency decreases as bacterial floc formation reduces. Temperatures lower than 10 °C also affect the performance of biological processes, especially when it comes to nitrification efficiency.
Biological activity is influenced by temperature because of the depth of penetration of oxygen into the floc or film. Oxygen penetration increases as temperature decreases, since oxygen is not used as quickly at floc surfaces and greater numbers of organisms per unit surface can react.
Variations in temperature can make a big difference in the composition of microbial communities. The dominance of a particular species shifts depending on the constantly changing composition and quality of the wastewater. As temperature changes, one group of microorganisms becomes less active and can even die off, whilst another group becomes dominant. Psychrophiles grow in the 0 to 20 °C range, with an optimum of 10 to 15 °C. Mesophiles, which are the species most found in wastewater treatment, grow in the 10 to 45 °C range, with an optimum of around 30 to 35 °C. Thermophiles, found in compost piles and other high-temperature environments, grow in the 40 to 75 °C range, with an optimum growth rate at 55 to 65 °C.
Temperature is, of course, just one environmental factor that affects wastewater treatment. But given its importance for biological processes, it’s imperative for facility operators to maintain the right temperatures. This is why process engineers use temperature as a key parameter in the designs of any biological wastewater treatment plants and adapt it to local climatic conditions. In cold environments, insulation of tanks is important to keep temperatures ideal. In warm climates, wastewater often needs to go through a cooling process.
We will consider other factors that influence clarifier efficiency in future posts and how this is connected to TOC measurement, so be sure to subscribe to our newsletter to get notified about updates.